This newer triple-gang two-wire Touch-Plate Classic ivory control switch station includes eighteen ivory light switches, a matching plastic switch plate frame, metal frame insert, mounting bracket and screws for a convenient, all-inclusive lighting unit.
Upgrading a Remcon, GE and Bryant lighting system? This 2-wire low voltage 18-switch unit can be used as replacements for any 3-wire low voltage 9-switch units, but please note that this panel fits a 3-gang box, but the 9-button Remcon master panel fit a 4-gang box. Be sure to order the 3 wire to 2 wire Touch Plate conversion guide, which will then be included free of charge.
- 2 wire low voltage system
- 1 amp @ 28 volts switch contact rating
- 18 momentary contact switches
- 7" x 5-1/8" metal switchplate
- includes wiring instruction diagram
- three 2" x 1-9/16" switch opening holes
- 3-9/32" screw hole spacing
- four 1-1/2" mounting screws
- CLAS3-1800A-IVR (CLA-18B-0L-IVR) by Touch Plate, satin ivory
- made in USA
Check out different switch styles at Touch-Plate Control Units & Wall Covers.
REMCON RETROFITS: If you are updating a Remcon low voltage lighting system master panel with either lighted or unlighted switches, then this is the correct replacement. LED lighted switches require a 4th wire for illuminating them which may not be available on Remcon systems so we recommend using this unlighted version. The center master switch would no longer work as that specific functionality was unique to Remcon hardware. Only the original 8 light switches would work with the eight pairs (ON/OFF) of new buttons on the Touch Plate control stations. Note that this Touch Plate panel fits a 3-gang box, but the Remcon 9-button master panel fit a 4-gang box. If there is no box in the wall, the 3-gang low voltage ring and the 3-gang 8" x 6" extender panel may allow you to cover up the opening with no sheetrock patching.