Single pole, single throw (SPST) Touch-Plate 3000 low voltage mechanical latch relay for Touch-Plate low voltage lighting systems can be used as an updated replacement part for older Touch-Plate low voltage systems that were installed from the 1940s to the 1980s. Specifically, this replacement 2-wire relay (model 3000) may be used to replace discontinued 1550-A, 1550-B, 2500-B, and 4000 Touchplate relays.
- 7" lead length, wire leads without plug (see the TPL-300PL if your relay plugs into the panel)
- black base: 1-7/8" L (terminal side) x 1-11/16" W x 31/32" H
- 1.75" H x 1" diameter cylinder; overall height from bottom of black base to top of cylinder is 2-3/4"
- cylinder is offset on base; center of cylinder is 9/16" from long edge (non-terminal side, back edge in photo) and 3/4" from the short side (left side in photo)
- includes 1" I.D. x 1/2" thick rubber grommet shown in photo
- 120/277/347 VAC 20 amp contact rating
- 1.0 HP 125 VAC, 20 A 125 VAC Tungsten
- 1.5 HP 250 VAC, 20A 277 VAC Ballast
- auxiliary contact rating of 1 amp at 30 volts, Tungsten
- constructed of silver alloy
- 3000 / 4000 relay base is 1" larger than older models 1550-A, 1550-B, 2500-B
- made in America; 1-year manufacturer warranty
- current replacement for Touchplates' old 1550A, 1550B, 2500B, and 4000 relays
Shop more authentic Hard-To-Find Touch-Plate Low Voltage Switches & Switch Plates from Kyle Switch Plates.
Q & A
If you hear a hissing noise coming from your relay, this means your relay needs to be replaced or the switch connected to that relay needs to be replaced. To determine which part is faulty, connect a working switch from a different area of your home to the switch that is connected to the buzzing relay. If the relay continues to buzz, then you know the relay needs to be replaced. If the relay stops buzzing, then you know the switch needs to be replaced.
Q. Can I substitute a GE or Remcon relay in my Touch Plate system?
No. The relays are too different. Touch-Plate relays are single coil, 28DVC latching relays whereas GE relays are dual coil and Remcon relays are single or dual coil with internal power supplies.
Q. My old 1550A relay had four wires coming out of it - two from the top of the cylinder and two from the bottom block. How do I install it with this replacement 3000 relay that only has two wires?
The old 1550A, 1550B, and 2500B relays had two low voltage wires coming out of the top cylinder that you would connect to your switches. The two wires coming out of the bottom were the ones you connected to the high voltage wires coming out from your wall electrical system. These new relays have screw terminals that eliminate the need to twist together and cap off the two sets of wires. You just attach the high voltage wires to the new screw terminals on the bottom block of the relay. This is a safer, more secure way to connect the wires than on the older relays. Because the high voltage connections are not polarized, it doesn't matter which way you connect the two high voltage wires to the two screw terminals - both terminals are the same, so either one can have the hot feed and the other the switch leg. Note that the bases on these new 3000 relays are a bit larger than the old ones so they might be a bit of a tight fit in the relay panel. If necessary, move the older relays to the back row and use the new 3000 relays in the front row where there is more room.
Q. My Touch-plate relay says it is 12 VDC, but replacement relays are 28V. Can I use these 3000 relays with them?
Yes. For a period of time in the past Touch-Plate was marking their relays with the lower voltage, even though they really had a higher voltage. Some were labeled as 12 VDC; others 14 VDC. But all Touch plate systems have always worked with 28 VDC transformers and transverters. (If you wish to confirm this on your end, simply check the output voltage on your unit.) So you may safely use a 3000 relay to replace a Touch Plate relay marked as 12V or 14V, and may use a new TPS-0120 transformer with either the new or the old relays.